Manufacturing Companies for Underground Heating Cable 1×70 Mm2+ 3×70 Mm2 Abc Cable - 600V Cu/Conner/Al Conductor ALuminum armor/thhn/thwn-2 MC cable PVC/Nylon Insulated MC cable with PVC sheathed – Cable
Manufacturing Companies for Underground Heating Cable 1×70 Mm2+ 3×70 Mm2 Abc Cable - 600V Cu/Conner/Al Conductor ALuminum armor/thhn/thwn-2 MC cable PVC/Nylon Insulated MC cable with PVC sheathed – Cable Detail:
- Place of Origin:
Shandong, China (Mainland)
- Brand Name:
- Model Number:
- Conductor Material:
- Insulation Material:
- Supply Ability:
- 10000000 Foot/Feet per Month
- Packaging Details
- per request
14 AWG through 1000kcmil Copper THHN/THWN-2 Insulated Singles. UL Listed. 600 Volts. Rated VW-1. Lightweight Aluminum Interlocked Armor.
This specification covers lightweight aluminum interlock armor type MC cable with soft annealed copper solid or stranded conductor,THHN/THWN insulated singles, conforming to Standard 1569 of Underwriters Laboratories, Inc. UL file No.E313205 .
Type MC cables are suitable for use as follows: branch, feeder and service power distribution in commercial, industrial, institutional, and multi-residential buildings. Power, lighting, control, and signal circuits. Type THHN/THWN conductors are rated 90℃ dry / 75℃ wet. They are permitted for 600V application.
Conductors: Soft annealed copper .
Insulation: Flame retardant PVC. Thickness: per UL83.
Number of conductors
black, white, red
black, white, red, blue
Conductor jacket: Nylon. Thickness: per UL83.
Cabling: Three or more conductors are assembled without fillers and wraped by a polyester binder tape. A marker tape is inserted under the binder tape.
Armor: Aluminum interlock armor is applied over the assembly.
Jacket: A flame retardant PVC jacket is optional.
Information on the marker tape or the jacket: AWG or kcmil size,conductor type letters,rated voltage,the name of the manufacturer,UL file number,characteristic,manufacture date,FEET.
Type MC Cable Data
Packaging Information: Coils or Reel
(1) When can I get a response?
We will reply to your inquiry as soon as possible, usually within 6 hours. You can call us directly if it is urgent.
(2). How can I get a sample?
you can require for samples after price confirmation. Samples in stock are free of charge, but the freight charge should be paid.
(3). What about the lead time for mass production?
It depends on the order quantity, the distance of transportation and so on. We suggest that you start inquiry two months before the date you would like to get the products at your country.
Please contact us for details about lead time and other issues.
We look forward to sincere cooperation with you!
Product detail pictures:
Related Product Guide:
Home Streaming Shootout: Nvidia Shield TV vs Roku Streaming Stick+ | Thhn Cable Nylon Jacket
Big Money’s Pro-Preformed Line Products Co (NASDAQ:PLPC) Sentiment In Q3 2018, now at 2.71 | Seo Cable
Our progress depends around the innovative machines, great talents and consistently strengthened technology forces for Manufacturing Companies for Underground Heating Cable 1×70 Mm2+ 3×70 Mm2 Abc Cable - 600V Cu/Conner/Al Conductor ALuminum armor/thhn/thwn-2 MC cable PVC/Nylon Insulated MC cable with PVC sheathed – Cable, The product will supply to all over the world, such as: Qatar, Oman, El Salvador, Many years of work experience, we have now realized the importance of providing good quality products and solutions and the best before-sales and after-sales services. Most problems between suppliers and clients are due to poor communication. Culturally, suppliers can be reluctant to question things they do not understand. We break down those barriers to ensure you get what you want to the level you expect, when you want it. faster delivery time and the product you want is our Criterion .
By Myrna from Paris - 2015.06.09 12:42
This manufacturers not only respected our choice and requirements, but also gave us a lot of good suggestions, ultimately， we successfully completed the procurement tasks.
By Eileen from Slovakia - 2015.07.27 12:26