MC cable Aluminum/Al conductors XLPE/XLP insulation/insulated Al armored for power/lighting/control/signal circuits awg/kcmil
- Place of Origin:
Shandong, China (Mainland)
- Brand Name:
- Model Number:
- Insulation Material:
- Conductor Material:
PVC jacket is optional
awg / kcmil
- Supply Ability:
- 10000000 Foot/Feet per Month
- Packaging Details
- per request
6AWG through 1000kcmil Aluminum cross-linked polyethylene XLPE insulation Insulated XHHW-2 Singles. UL Listed. 600 Volts. Rated VW-1. Lightweight Aluminum Interlocked Armor. PVC jacket
This specification covers lightweight aluminum interlock armor type MC cable with Compact strand 8000 series aluminum alloy conductors,cross-linked polyethylene XLPE insulation Insulated XHHW-2 Singles, conforming to Standard 1569 of Underwriters Laboratories, Inc. UL file No.E313205 .
Type MC cables Suitable for use in branch, feeder and service power distribution under high ambient temperature in commercial, industrial, institutional, casinos and multi-residential buildings; for power, lighting, control and signal circuits; in concealed or exposed installations; in environmental air-handling spaces per NEC 300.22; in places of assembly per NEC 518.4 and theaters per NEC 520.5; in aerial applications when attached to a messenger; for installation in cable tray and approved raceways; under raised floors for IT equipment per NEC 645.5(D) and 645.5(D)(2); Class I Div 2, Class II Div 2, Class III Div 1 hazardous locations.
Conductors: Compact strand 8000 series aluminum alloy conductors
Insulation: Color coded cross-linked polyethylene XLPE insulation. The cable ground is either bare or has green insulation. Thickness: per UL44.
Cabling: Three or more conductors are assembled without fillers and wraped by a polyester binder tape. A marker tape is inserted under the binder tape.
Armor: Aluminum interlock armor is applied over the assembly.
Jacket: An overall black polyvinyl chloride PVC jacket, which is heat, moisture and sunlight resistant.
Information on the marker tape or the jacket: AWG or kcmil size, conductor type letters, rated voltage, the name of the manufacturer, UL file number, characteristic, manufacture date, FEET.
Type Aluminum Conductor–Jacketed MC Cable Data
Packaging Information: Coils or Reel
Founded in 1950, Qingdao Cable Co., Ltd.,former Qingdao Cable Works, has the experience of more than 60 years in the production of wires and cables, with the registered trademark of “Qing Kai”,”Qing Lan”.
As the Enterprise of High and New Technology of China, Qingdao Cable Co., Ltd. Has been manufacturing high quality products with the advanced equipments and complete inspection instruments. The company has been awarded the certificate of approval of ISO9001, ISO14001, OHSAS18000, and has been certified by the multinational companies of GE, Motorola, etc. Several kinds of products are listed by American UL and Chinese CCC. The company can produce and develop products in accordance with such standards as GB, IEC, UL, JS, VDE, SAE, and the purchasers’ requirement as well.