OEM Manufacturer Ul Standard Cable - Type THHN wire Solid or stranded building wire and cable Cu/Al conductor pcv insulation and Nylon Sheath – Cable
OEM Manufacturer Ul Standard Cable - Type THHN wire Solid or stranded building wire and cable Cu/Al conductor pcv insulation and Nylon Sheath – Cable Detail:
- Place of Origin:
Shandong, China (Mainland)
- Brand Name:
- Model Number:
- Insulation Material:
- Conductor Material:
14/12/10/8/6/4/3/2/1 1/0 2/0 3/0 4/0 250/300/400/500/600 awg or kcmil
- Supply Ability:
- 10000000 Foot/Feet per Month
- Packaging Details
- per request
AL THHN/THWN2/T90 600V PVC/Nylon Insulation
* Ampacities for not more than three conductors in raceway, based on ambient temperature of 30°C per
Table 310-15 of the 2011 NEC
Application: THHN / THWN-2 / T90 cables are primarily use for power distribution. The cables may be used in wet or dry locations, with ambient temperatures not exceeding 90°C. Voltage rating for cable is 600V.
Conductors: Compact soft drawn bare 8000 series aluminum, with Class B stranding
Insulation: Low coefficient of friction abrasion, heat, sunlight, and moisture resistant polyvinyl chloride PVC
Jacket: A clear abrasion, heat, sunlight, moisture resistant and low coefficient of friction nylon jacket.
Standard stock colors include: black, red, blue, white, brown, orange, yellow, gray,purple and green.
Standards: meet or exceed the following standards:
UL standard 83, CUL CSA C22.2 No. 75
1/0 & larger are rated for CT use Requirements of the National Electrical Code NEMA WC-70
Founded in 1950, Qingdao Cable Co., Ltd.,former Qingdao Cable Works, has the experience of more than 60 years in the production of wires and cables, with the registered trademark of “Qing Kai”,”Qing Lan”.
As the Enterprise of High and New Technology of China, Qingdao Cable Co., Ltd. Has been manufacturing high quality products with the advanced equipments and complete inspection instruments. The company has been awarded the certificate of approval of ISO9001, ISO14001, OHSAS18000, and has been certified by the multinational companies of GE, Motorola, etc. Several kinds of products are listed by American UL and Chinese CCC. The company can produce and develop products in accordance with such standards as GB, IEC, UL, JS, VDE, SAE, and the purchasers’ requirement as well.
(1) When can I get a response?
We will reply to your inquiry as soon as possible, usually within 6 hours. You can call us directly if it is urgent.
(2). How can I get a sample?
you can require for samples after price confirmation. Samples in stock are free of charge, but the freight charge should be paid.
(3). What about the lead time for mass production?
It depends on the order quantity, the distance of transportation and so on. We suggest that you start inquiry two months before the date you would like to get the products at your country.
Please contact us for details about lead time and other issues.
We look forward to sincere cooperation with you!
Product detail pictures:
Related Product Guide:
Renewable resort: Greek island to run on wind, solar power | Community | Swa Armored Xlpe Cable
400-kW solar+storage carport project completed in Hawaii for Spectrum cable | Thhn Cable Nylon Jacket
Our workforce through professional training. Skilled professional knowledge, solid sense of service, to fulfill the services demands of consumers for OEM Manufacturer Ul Standard Cable - Type THHN wire Solid or stranded building wire and cable Cu/Al conductor pcv insulation and Nylon Sheath – Cable, The product will supply to all over the world, such as: Estonia, Serbia, Detroit, Our company has always insisted on the business principle of "Quality, Honest, and Customer First" by which we have won the trust of clients both from at home and abroad. If you are interested in our products, please do not hesitate to contact us for further information.
By Paula from Iraq - 2015.09.19 18:37
Wide range, good quality, reasonable prices and good service, advanced equipment, excellent talents and continuously strengthened technology forces，a nice business partner.
By Fay from Surabaya - 2016.03.28 16:34